Viessmann Manufacturing Company Inc. recalls Viessmann Vitodens 200-W boiler models B2HB-45 and B2HB-57
- Starting date:
- February 25, 2016
- Posting date:
- February 25, 2016
- Type of communication:
- Consumer Product Recall
- Household Items
- Source of recall:
- Health Canada
- Fire Hazard
- General Public
- Identification number:
Joint recall with Health Canada, the United States Consumer Product Safety Commission (US CPSC), and Viessmann Manufacturing Company Inc.
Viessmann Vitodens 200-W boiler models B2HB-45 and B2HB-57
This recall involves Vitodens 200-W gas fired boiler models used for space or domestic hot water heating. The product name and model number can be found on the boiler rating plate located on the left side of the boiler cover, while the serial number can be found on a separate label under the boiler cover on the left hand side of the boiler.
|Product Number||Model Numbers||Serial Numbers|
|Vitodens 200-W||B2HB-45||7554703501001105 to 7554703501369106|
|B2HB-57||7554704501001102 to 7554704501411109|
The flue gas baffle used inside the heat exchanger assembly may become dislodged due to a mechanical fastener slipping, causing higher than normal flue gas temperatures to enter the flue gas collector and the venting system resulting in the F1 fault. The venting system may melt and cause the flue gases to escape into the house posing a risk of fire and increased carbon monoxide levels.
Health Canada has not received any reports of consumer incidents or injuries related to the use of these boilers.
Viessmann Manufacturing has received 10 reports of incidents involving the boilers. Seven of these have been reported from Canada. No injuries have been reported in any of the incidents.
Approximately 141 units were sold in Canada and around 165 units were distributed in the United States.
Time period sold
The recalled products were sold from September 1, 2015 to December 22, 2015 in Canada and the United States.
Place of origin
Manufactured in Germany.
Viessmann Werke GmbH & Co KG
Viessmann Manufacturing Company Inc.
What you should do
Consumers with recalled boilers are advised to contact the installer or the wholesaler/distributor from whom they purchased the boiler or Viessmann Manufacturing immediately in order to schedule a free boiler safety inspection. Consumers who continue the use of these boilers while awaiting inspection should have a working carbon monoxide alarm installed outside of sleeping areas in the home.
Consumers may view the release by the US CPSC on the Commission's website.
Please note that the Canada Consumer Product Safety Act prohibits recalled products from being redistributed, sold or even given away in Canada.
Health Canada would like to remind Canadians to report any health or safety incidents related to the use of this product or any other consumer product or cosmetic by filling out the Consumer Product Incident Report Form.
This recall is also posted on the OECD Global Portal on Product Recalls website. You can visit this site for more information on other international consumer product recalls.
- Date modified: