Recalls and alerts more than 4 years old are automatically archived. While this information can still be accessed in the database, it has not been altered or updated since it was archived. Web pages that are archived on the Web are not subject to the Government of Canada Web Standards. As per the Communications Policy of the Government of Canada, you can request alternate formats by contacting us.
Visonic Ltd. recalls PowerMax Express and PowerMax Complete panels
- Starting date:
- June 24, 2015
- Posting date:
- June 24, 2015
- Type of communication:
- Consumer Product Recall
- Tools and Electrical Products
- Source of recall:
- Health Canada
- Electrical Hazard
- General Public
- Identification number:
Visonic PowerMax Express and PowerMax Complete Panels
This recall involves the Visonic PowerMax Express and PowerMax Complete control panels with software version 15. The control panels are professionally installed, and have an LCD display and icon-based keypad.
|Catalog No.||Product Name||Serial Number Range||Dates of Manufacture||EAN Code|
|0-101312||PMAX EXPRESS (315) 211 PRE-ENR GSM KIT||5109005125 through 2312020274||March 2012 – June 2013||7290103301828|
|0-101342||PMAX EXPRESS (315) 211 PRE-ENR KIT||14209044412 through 2113A06254||March 2012 – August 2013||7290103302313|
|0-101473||PM EXRESS(315) SURVEILLANCE PL QF KIT||4012016495 through 4012016497||October 2012 – March 2013||7290103303686|
|0-101692||PM COMPLETE USA (315) GSM 3-1-1 KIT||1411025864||July 2012||7290103306472|
|0-101693||PM COMPLETE USA (315) 3-1-1 KIT||1411025774 through 113016311||March 2012 – January 2013||7290103306465|
Visonic has become aware of an issue affecting PowerMax Express PowerMax Complete panels with software version 15 used in these devices. The external memory in these devices, which contains panel configuration, LCD texts and predefined SMS messages, can be eventually overwritten by the device’s event log file. This condition takes approximately one to three years to occur (depending on daily levels of system activity). The resulting impact on the panel’s operation is that false events, such as power failure and zone trouble, will be displayed on the panel and will be reported to the central monitoring station; and panels that are configured to send SMS messages, will send corrupted SMS messages. Eventually, real alarm events will not be sent to the central monitoring station, and periodic tests done by the end users will fail. Safety detectors such as smoke, gas, etc. are unaffected and will sound a local alarm if an event occurs.
Neither Health Canada nor Visonic has received any reports of consumer incidents or injuries related to the use of this product.
Approximately 69 units were sold in Canada through professional alarm installers.
Time period sold
The recalled panels were sold from February 2012 to February 2014.
Place of origin
Manufactured in Israel.
What you should do
Consumers with affected units should contact their dealer/installer/distributor or contact Visonic to receive instructions for repair of their panel.
For more information, consumers may contact Visonic’s support center (North America) toll free at 1-844-888-2391, from 8:30 a.m. to 6:00 p.m. EST, Monday through Friday.
Please note that the Canada Consumer Product Safety Act prohibits recalled products from being redistributed, sold or even given away in Canada.
Health Canada would like to remind Canadians to report any health or safety incidents related to the use of this product or any other consumer product or cosmetic by filling out the Consumer Product Incident Report Form.
- Date modified: